(5) Refer to air-conditioner unit operating
service power load center (A6).
procedure, TM 5-4120-308-15 for shutdown of air-
(7) Turn off ac service power main circuit
(6) Turn off each circuit breaker on the ac
(8) Turn off van incandescent light switch.
Section III. OPERATION UNDER UNUSUAL
moisture and fungi. Wipe all moisture and fungi from the
Operation in Extreme Climates
equipment with a lint-free cloth.
The assemblages of the AN/MYK-8(V) (*) are fully
Emergency Power Shutdown and Restart
insulated and weatherproofed for operation in hot, cold,
a. Emergency Shutdown. To remove pIower from
or moderate climates. The shelter facility provides
complete protection from the elements for personnel and
the vans in an emergency condition, per-form the
equipment; however, under extreme conditions, the
following precautions are necessary.
(1) Turn the ADP MAIN circuit breaker to OFF
a. Cold Climates. Extreme cold causes cables and
to remove power from all ADP equipment.
wires to become hard, brittle, and difficult to handle. Be
(2) Turn the ac service plower main circuit
careful when handling the cables and connecting them to
breaker to OFF.
b. Restart. To apply power to the vans after an
the assemblage so that kinks and unnecessary loops will
not result in permanent damage. Make sure binding
emergency shutdown, perform the following procedure:
posts and connectors in the entrance boxes are free of
frost, snow, and ice. Replace the covers on receptacles,
and close the entrance box covers when they are not in
If the ADP system has been shutdown
use. Replace the connector cover as soon as a cable is
under emergency conditions either l)y an
disconnected. Never drag or place an open connector in
ADP maintenance power breaker in any
van being tripped, or by the
b. Hot Climates. In hot, dry climates, connectors,
from dust and dirt.
Replace the covers on the
SWITCH (CPU) be-ing activated, call
connectors and receptacles and close the covers on
qualified maintenance personnel only to
entrance boxes when they are not in use. Never place
reset EPO sequencing equipment, then
an open connector on the ground. When outside
bring the ADP system up.
temperatures are extremely high, install the sunshades
(2) To restart the OL-88(V) (*)/MYK-8 (V),
lower internal van temperatures as much as 10 degrees.
c. Warm, Damp Climates.
In warm, damp
the OL-89 (V) (*) /MYK-8(V), perform (1) through (14) of
climates, the equipment is subject to damage from
Section IV. PREPARATION FOR MOVEMENT
a. Shut down system equipment according to
c. Perform interval pack operation in accordance
b. Move ADPE to transport position as follows:
with the applicable equipment publication (appx A).
(1) Clear the floor area of the van in front of the
d. Remove signal cables (fig. FO-1) from van 1 and
equipment rack and lift hydraulic rail cover plates.
2 and install covers (performed by ADPE maintenance
(2) Depress the START MOTOR PUMP
e. Shut down engine generator sets in accordance
(3) Depress and hold the OUT button. Re-
with instructions in TM 5-6115-293-12.
lease the button when the rack has stopped in the center
f. Remove all power cables connected to the
of the van. Repeat for each unit to be